Федеральная служба по экологическому, технологическому и атомному надзору

Утверждено приказом Федеральной службы по экологическому, технологическому и атомному и атомному надзору от 30 августа 2021 г. № 288.

Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух. РБ-106-21

Введено в действие с 30 августа 2021 г.

© Москва 2021.

Руководство по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух»

Руководство по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух» (далее — Руководство по безопасности) разработано в соответствии со статьей 6 Федерального закона от 21 ноября 1995 г. № 170-ФЗ «Об использовании атомной энергии» в целях содействия соблюдению требований федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности атомных станций» (НП-001-15), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 17 декабря 2015 г. № 522 (зарегистрирован Минюстом России 2 февраля 2016 г., регистрационный № 40939), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности объектов ядерного топливного цикла» (НП-016-05), утвержденных постановлением Федеральной службы по экологическому, технологическому и атомному надзору от 2 декабря 2005 г. № 11 (зарегистрировано Минюстом России 1 февраля 2006 г., регистрационный № 7433), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности исследовательских ядерных установок» (НП-033-11), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 июня 2011 г. № 348 (зарегистрирован Минюстом России 29 августа 2011 г., регистрационный № 21700), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности судов и других плавсредств с ядерными реакторами» (НП-022-17), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 4 сентября 2017 г. № 351 (зарегистрирован Минюстом России 27 сентября 2017 г., регистрационный № 48344), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности радиационных источников» (НП-038-16), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 28 сентября 2016 г. № 405 (зарегистрирован Минюстом России 24 октября 2016 г., регистрационный № 44120), и федеральных норм и правил в области использования атомной энергии «Безопасность при обращении с радиоактивными отходами. Общие положения» (НП-058-14), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 5 августа 2014 г. № 347 (зарегистрирован Минюстом России 14 ноября 2014 г., регистрационный № 34701).

Настоящее Руководство по безопасности содержит рекомендуемые Федеральной службой по экологическому, технологическому и атомному надзору методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух.

Руководство по безопасности распространяется на объекты использования атомной энергии, осуществляющие выбросы радиоактивных веществ в атмосферный воздух.

Настоящее Руководство по безопасности предназначено для применения организациями, осуществляющими разработку проектов нормативов выбросов радиоактивных веществ в атмосферный воздух, а также организациями, осуществляющими экспертизу указанных проектов.

Выпускается взамен РБ-106-15 «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух», утвержденного приказом Ростехнадзора от 11 ноября 2015 г. № 458.

Руководство по безопасности разработано коллективом авторов в составе: А. В. Курындин, А. С. Шаповалов, Н. Б. Тимофеев (ФБУ «НТЦ ЯРБ»).

Оглавление

I. Общие положения

1. Руководство по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух» (РБ-106-21) (далее — Руководство по безопасности) разработано в соответствии со статьей 6 Федерального закона от 21 ноября 1995 г. № 170-ФЗ «Об использовании атомной энергии» в целях содействия соблюдению требований федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности атомных станций» (НП-001-15), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 17 декабря 2015 г. № 522 (зарегистрирован Министерством юстиции Российской Федерации 2 февраля 2016 г., регистрационный № 40939), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности объектов ядерного топливного цикла» (НП-016-05), утвержденных постановлением Федеральной службы по экологическому, технологическому и атомному надзору от 2 декабря 2005 г. № 11 (зарегистрировано Министерством юстиции Российской Федерации 1 февраля 2006 г., регистрационный № 7433), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности исследовательских ядерных установок» (НП-033-11), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 июня 2011 г. № 348 (зарегистрирован Министерством юстиции Российской Федерации 29 августа 2011 г., регистрационный № 21700), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности судов и других плавсредств с ядерными реакторами» (НП-022-17), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 4 сентября 2017 г. № 351 (зарегистрирован Министерством юстиции Российской Федерации 27 сентября 2017 г., регистрационный № 48344), федеральных норм и правил в области использования атомной энергии «Общие положения обеспечения безопасности радиационных источников» (НП-038-16), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 28 сентября 2016 г. № 405 (зарегистрирован Министерством юстиции Российской Федерации 24 октября 2016 г., регистрационный № 44120), и федеральных норм и правил в области использования атомной энергии «Безопасность при обращении с радиоактивными отходами. Общие положения» (НП-058-14), утвержденных приказом Федеральной службы по экологическому, технологическому и атомному надзору от 5 августа 2014 г. № 347 (зарегистрирован Министерством юстиции Российской Федерации 14 ноября 2014 г., регистрационный № 34701).

2. Настоящее Руководство по безопасности содержит рекомендуемые Федеральной службой по экологическому, технологическому и атомному надзору методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух.

3. Настоящее Руководство по безопасности распространяется на объекты использования атомной энергии, осуществляющие выбросы радиоактивных веществ в атмосферный воздух.

4. Настоящее Руководство по безопасности предназначено для применения организациями, осуществляющими разработку проектов нормативов выбросов радиоактивных веществ в атмосферный воздух, а также организациями, осуществляющими экспертизу указанных проектов.

5. Требования федеральных норм и правил в области использования атомной энергии могут быть выполнены с использованием иных способов, чем те, которые содержатся в настоящем Руководстве по безопасности, при обоснованности выбранных способов.

II. Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух

6. Параметры, необходимые для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух, рекомендуется рассчитывать в соответствии с соотношениями, изложенными в настоящем Руководстве по безопасности.

7. Для выполнения расчетов функций перехода, связывающих годовую эффективную дозу с выбросами радионуклидов, предусмотренных разделом III Методики разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух, утвержденной приказом Федеральной службы по экологическому, технологическому и атомному надзору от 7 ноября 2012 г. № 639 (зарегистрирован Министерством юстиции Российской Федерации 18 января 2013 г., регистрационный № 26595) (далее — Методика), рекомендуется руководствоваться положениями данного раздела настоящего Руководства по безопасности.

8. Соотношение для расчета функции перехода, связывающей активность годового выброса радионуклида r из i-го источника с годовой эффективной дозой облучения населения, приведенное в пункте 14 Методики, рекомендуется представить в следующем виде:

где:

 — функция перехода для расчета годовой дозы внешнего облучения от облака, Зв/Бк;

 — функция перехода для расчета годовой дозы внешнего облучения от радиоактивного загрязнения поверхности земли, Зв/Бк;

 — функция перехода для расчета годовой дозы внутреннего облучения от вдыхания радионуклидов (ингаляционный путь), Зв/Бк;

 — функция перехода для расчета годовой дозы внутреннего облучения от потребления пищевых продуктов, содержащих радионуклиды (пероральный путь), Зв/Бк;

x — расстояние от источника, м;

n — номер румба, определяющего направление распространения выброса.

9. Расчет функции перехода  рекомендуется производить по формуле:

где:

 — коэффициент дозового преобразования при внешнем облучении человека от облака для радионуклида r, (Звм3)/(сБк);

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы для радионуклида r на расстоянии x от i-го организованного источника в n-ом румбе, с/м3, для расчета которого рекомендуется использовать формулу (1) или (2) приложения № 1 к настоящему Руководству по безопасности;

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы на расстоянии x от i-го неорганизованного площадного источника в n-ом румбе, с/м3, для расчета которого рекомендуется использовать формулу (6) приложения № 1 к настоящему Руководству по безопасности.

Рекомендуемые численные значения коэффициентов  приведены в таблице № 1 приложения № 2 к настоящему Руководству по безопасности.

10. Расчет функции перехода  рекомендуется производить по формуле:

где:

 — среднегодовой метеорологический фактор сухого осаждения радионуклида r на подстилающую поверхность на расстоянии x от i-го источника выброса в n-ом румбе, м-2;

 — среднегодовой метеорологический фактор влажного выведения радионуклида r из облака на подстилающую поверхность на расстоянии x от i-го источника выброса в n-ом румбе, м-2;

 — коэффициент дозового преобразования при внешнем облучении человека от радиоактивно загрязненной поверхности без учета глубинного распределения для радионуклида r, (Звм2)/(сБк);

 — постоянная радиоактивного распада радионуклида r, с-1;

 — постоянная спада мощности дозы -излучения от загрязненной поверхности земли за счет экранирования верхними слоями почвы, диффузии вглубь и выведения радионуклидов из нее за счет различных процессов, кроме радиоактивного распада, с-1 (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 1,2710-9 с-1).

Рекомендуемые численные значения дозовых коэффициентов приведены в таблице № 1 приложения № 2 к настоящему Руководству по безопасности.

Рекомендуемые методы расчета величин  и  для различных типов источников выбросов (организованные, неорганизованные площадные источники) приведены в приложении № 1 к настоящему Руководству по безопасности.

11. Расчет функции перехода  рекомендуется производить по формуле:

где:

 — интенсивность вдыхания для лиц возрастной группы, которая является критической по поступлению радионуклида r за счет ингаляции, м3/с;

 — коэффициент дозового преобразования при ингаляции радионуклида r для возрастной группы, которая является критической по поступлению радионуклида r за счет ингаляции, Зв/Бк;

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы для радионуклида r на расстоянии x от i-го организованного источника в n-ом румбе, с/м3, для расчета которого рекомендуется использовать формулу (1) или (2) приложения № 1 к настоящему Руководству по безопасности;

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы на расстоянии x от i-го неорганизованного площадного источника в n-ом румбе, с/м3, для расчета которого рекомендуется использовать формулу (6) приложения № 1 к настоящему Руководству по безопасности.

Рекомендуемые значения  для различных возрастных групп населения приведены в таблице № 2 приложения № 2 к настоящему Руководству по безопасности.

Значения коэффициентов  для различных возрастных групп населения рекомендуется принимать в соответствии с положениями нормативных актов Российской Федерации, в которых они установлены, а в случае отсутствия таких нормативных актов — в соответствии с рекомендациями международных организаций в области использования атомной энергии.

Для определения возрастной группы населения, являющейся критической по ингаляционному поступлению радионуклида r, рекомендуется использовать следующий алгоритм:

1) для каждой возрастной группы населения оценить значение произведения ∙;

2) выполнить сравнение между собой полученных значений и принять в качестве критической ту возрастную группу населения, для которой упомянутое выше значение произведения является максимальным.

12. Расчет функции перехода  для всех радионуклидов, за исключением 3Н и 14С, рекомендуется проводить по формуле:

где:

Ir,f — годовое потребление продукта f лицом из возрастной группы, которая является критической по пероральному поступлению радионуклида r с пищевыми продуктами (рекомендуется выделить три группы продуктов — «молоко», «мясо», «овощи»), значение которого рекомендуется определять на основе данных местных натурных исследований, кг/год;

 — коэффициент дозового преобразования при пероральном поступлении радионуклида r для возрастной группы, являющейся критической по пероральному поступлению радионуклида r, Зв/Бк;

 — коэффициент перехода «выпадение из атмосферы — поступление в продукт» радионуклида r в продукт питания f по воздушному пути, рассчитываемый для овощной, молочной и мясной пищевых цепочек, м2·год/кг;

 — коэффициент перехода «выпадение из атмосферы — поступление в продукт» радионуклида r в продукт питания f по корневому пути, рассчитываемый для овощной, молочной и мясной пищевых цепочек, м2·год/кг;

αf — доля потребления продуктов местного сельскохозяйственного производства в общем потреблении продуктов (в случае отсутствия данных местных натурных исследований рекомендуется консервативно принимать равной 1; в случае отсутствия потребления населением сельскохозяйственной продукции, произведенной в районе влияния организации, осуществляющей выбросы, при условии, что это подтверждено официальными статистическими данными, данный параметр рекомендуется принимать равным 0);

 — среднегодовой метеорологический фактор сухого осаждения радионуклида r на подстилающую поверхность на расстоянии x от i-го источника выброса в n-ом румбе, м-2;

 — среднегодовой метеорологический фактор влажного выведения радионуклида r из облака на подстилающую поверхность на расстоянии x от i-го источника выброса в n-ом румбе, м-2.

Значения коэффициентов  для различных возрастных групп населения рекомендуется принимать в соответствии с положениями нормативных актов Российской Федерации, в которых они установлены, а в случае отсутствия таких нормативных актов — в соответствии с рекомендациями международных организаций в области использования атомной энергии.

Для определения возрастной группы населения, являющейся критической по пероральному поступлению радионуклида r с продуктом питания f, рекомендуется использовать следующий алгоритм:

1) для каждой возрастной группы населения оценить значение суммы произведений ;

2) выполнить сравнение между собой полученных значений и принять в качестве критической ту возрастную группу населения, для которой упомянутое выше значение является максимальным.

13. Коэффициенты перехода для овощной цепочки для радионуклидов, отличных от 234U, 235U и 238U, рекомендуется рассчитывать по формулам:

где:

α2 — фактор удержания для овощей, потребляемых в пищу человеком, рекомендуется принимать равным 0,3 м2/кг (сырого веса);

te — период времени (в течение вегетационного периода), в течение которого происходит улавливание радиоактивных выпадений поверхностью растений (в случае отсутствия данных местных натурных исследований рекомендуется принимать равным 30 сут);

 — постоянная распада радионуклида r, сут-1;

λw — постоянная, характеризующая процессы снижения содержания радионуклидов на поверхности растений за счет всех процессов, за исключением радиоактивного распада (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 0,05 сут-1);

λs,r — постоянная, характеризующая процессы снижения содержания радионуклидов в корневом слое почвы за счет всех процессов, за исключением радиоактивного распада (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 0,00014 сут-1 для изотопов цезия и стронция и равной нулю для остальных радионуклидов);

Fνr — коэффициент перехода радионуклида r из корневого слоя почвы в съедобную часть растения, кг (сухой почвы)/кг (сырой массы растения);

tb — параметр, равный 1,1∙104 суток (30 лет);

ρ — поверхностная плотность корневого слоя почвы (в случае отсутствия данных местных натурных исследований рекомендуется принимать в соответствии с таблицей № 3 приложения № 2 настоящего Руководства по безопасности), кг/м2;

th — время между сбором урожая и потреблением овощного продукта (в случае отсутствия фактических данных рекомендуется принимать равным 90 сут).

14. Для изотопов 234U, 235U и 238U, присутствующих в выбросе, рекомендуется коэффициенты перехода по овощной цепочке рассчитывать по формулам:

15. Коэффициенты перехода по молочной и мясной цепочкам рекомендуется рассчитывать по формулам:

где:

λr — постоянная распада, сут-1;

 — суточная масса корма, потребляемая молочным скотом (в случае отсутствия фактических данных рекомендуется принимать равной 16 кг (сухого вещества)/сут);

 — суточная масса корма, потребляемая мясным скотом (в случае отсутствия фактических данных рекомендуется принимать равной 12 кг (сухого вещества)/сут);

– относительная доля активности радионуклида r, которая попадает в литр молока от суточного потребления корма скотом, сут/л;

 — относительная доля активности радионуклида r, которая попадает в килограмм мяса от суточного потребления корма скотом, сут/кг;

tm — время между надоем молока и его потреблением (в случае отсутствия фактических данных рекомендуется принимать равным 1 сут);

tf — время между забоем скота и потреблением мяса (в случае отсутствия фактических данных рекомендуется принимать равным 20 сут);

 — коэффициент перехода «выпадение из атмосферы — поступление в корм» радионуклида r по воздушному пути, м2·год/кг;

 — коэффициент перехода «выпадение из атмосферы — поступление в корм» радионуклида r по корневому пути, м2·год/кг.

16. Величины  и  рекомендуется рассчитывать по формулам:

где:

коэффициент  рассчитывается аналогично коэффициенту  со следующими параметрами: th = 0, te = 30 сут, с использованием параметра α1, равного 3 м2/кг (сухого веса), вместо α2;

коэффициент  рассчитывается аналогично коэффициенту  со следующими параметрами: th = 90 сут; te = 30 сут; с использованием параметра α1, равного 3 м2/кг (сухого веса), вместо α2;

коэффициент  рассчитывается аналогично коэффициенту  со следующими параметрами: th = 0; с использованием Fν1r вместо Fνr;

коэффициент  рассчитывается аналогично коэффициенту  со следующими параметрами: th = 90 сут; с использованием Fν1r вместо Fνr;

fp — доля года, в течение которой скот питается подножным кормом (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 0,7).

Рекомендуемые значения Fνr, Fν1r, ,  приведены в таблице № 4 приложения № 2 к настоящему Руководству по безопасности.

17. При отсутствии достоверно известных данных о годовом потреблении пищевых продуктов питания лицами из различных возрастных групп для определения возрастной группы, являющейся на основе рекомендаций пункта 12 настоящего Руководства по безопасности критической по пероральному поступлению радионуклида r, рекомендуется оценивать потребление с помощью соотношения:

где:

g — возрастная группа (данная переменная принимает следующие значения: 2 — дети в возрасте 1–2 лет; 3 — дети в возрасте 2–7 лет; 4 — дети в возрасте 7–12 лет; 5 — дети в возрасте 12–17 лет; 6 — взрослые (старше 17 лет);

Eg — суточные энергетические затраты для возрастной группы g, ккал/сут;

Eg=6 — суточные энергетические затраты для возрастной группы «взрослые», ккал/сут.

If,g=6 — годовое потребление продукта f лицом из возрастной группы «взрослые» по данным местных натурных исследований, кг/год.

В случае отсутствия данных местных натурных исследований рекомендуется годовые потребления продуктов лицом из возрастной группы «взрослые» принимать в соответствии с Рекомендациями по рациональным нормам потребления пищевых продуктов, отвечающих современным требованиям здорового питания, утвержденными приказом Министерства здравоохранения Российской Федерации от 19 августа 2016 г. № 614. Значения суточных энергетических затрат для различных возрастных групп рекомендуется принимать согласно таблице № 5 приложения № 2 к настоящему Руководству по безопасности.

18. Внутри санитарно-защитной зоны (далее — СЗЗ) рекомендуется принимать равной нулю  в случае, если пищевые продукты и корма для скота в СЗЗ не производятся и если выпас скота на территории СЗЗ не осуществляется.

19. При отсутствии достоверно известных данных о долях потребления продуктов местного сельскохозяйственного производства αf в общем потреблении продуктов функцию перехода, связывающую активность выброса 3H из i-го источника с годовой эффективной дозой облучения населения за счет поступления трития ингаляционно, перорально и через кожные покровы, рекомендуется рассчитывать по формуле:

где:

– дозовый коэффициент для трития, значение которого рекомендуется принимать равным 2,6·10-8 (Зв·л)/(Бк·год)*;

H — абсолютная влажность воздуха, значение которой в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 6∙10-3 л/м3;

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы для трития, выбрасываемого из i-го организованного источника, c/м3 (для расчета фактора разбавления рекомендуется использовать формулу (1) или (2) приложения № 1 к настоящему Руководству по безопасности);

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы на расстоянии x от i-го неорганизованного площадного источника в n-ом румбе, с/м3 (для расчета фактора разбавления рекомендуется использовать формулу (6) приложения № 1 к настоящему Руководству по безопасности).

* Значение дозового коэффициента для 3H принято в соответствии с Generic Models for use in Assessing the Impact of Discharges of Radioactive Substances to the Environment / Safety Reports. — Series № 19. — Vienna: IAEA, 2000.

При наличии достоверно известных данных о долях потребления продуктов местного сельскохозяйственного производства αf в общем потреблении продуктов для расчета функции перехода, связывающей активность выброса 3H из i-го источника с годовой эффективной дозой облучения населения, рекомендуется использовать соотношения, учитывающие доли потребления αf.

20. При отсутствии достоверно известных данных о долях потребления продуктов местного сельскохозяйственного производства αf в общем потреблении продуктов функцию перехода, связывающую активность выброса 14С из i-го источника с годовой эффективной дозой облучения населения за счет воздействия углерода, поступающего в организм человека пероральным путем, рекомендуется определять следующим образом:

где:

 — дозовый коэффициент для углерода, (Зв·г)/(Бк·год), значение которого рекомендуется принимать равным 5,6·10-5 (Зв·г)/(Бк·год)*;

– параметр, который рекомендуется принять равным 1,8·10-1 г/м3;

 — среднегодовой метеорологический фактор разбавления для углерода, выбрасываемого из i-го организованного источника, c/м3 (для расчета фактора разбавления рекомендуется использовать формулу (1) или (2) приложения № 1 к настоящему Руководству по безопасности);

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы на расстоянии x от i-го неорганизованного площадного источника в n-ом румбе, с/м3 (для расчета фактора разбавления рекомендуется использовать формулу (6) приложения № 1 к настоящему Руководству по безопасности).

* Значение дозового коэффициента для 14C принято в соответствии с Generic Models for use in Assessing the Impact of Discharges of Radioactive Substances to the Environment / Safety Reports. — Series № 19. — Vienna: IAEA, 2000.

При наличии достоверно известных данных о долях потребления продуктов местного сельскохозяйственного производства αf в общем потреблении продуктов для расчета функции перехода, связывающей активность выброса 14C из i-го источника с годовой эффективной дозой облучения населения, рекомендуется использовать соотношения, учитывающие доли потребления αf.

21. При расчете функции перехода для 3H в форме пара HTO и 14С в формах, отличных от аэрозольной, фактор истощения шлейфа выброса за счет радиоактивного распада, сухого осаждения и вымывания атмосферными осадками, используемый в формулах (1), (2) и (5) приложения № 1 к настоящему Руководству по безопасности, рекомендуется принять равным единице.

III. Рекомендации по определению источников выбросов и радионуклидов, для которых должны быть установлены нормативы, при разработке нормативов предельно допустимых выбросов

22. Определение источников выбросов и радионуклидов, для которых в соответствии с пунктом 7 Методики должны быть установлены нормативы, рекомендуется выполнять на основе рекомендаций настоящего раздела.

23. Для определения необходимости установления нормативов для конкретного источника выбросов рекомендуется выполнить оценку обусловленной им годовой эффективной дозы облучения населения без учета рассеивания. В случае если рассчитанное значение превышает установленное в пункте 7 Методики значение 10 мкЗв/год, для данного источника должны быть установлены нормативы предельно допустимых выбросов.

24. Годовую эффективную дозу облучения населения без учета рассеивания, создаваемую i-м источником выброса, рекомендуется оценивать с помощью следующего соотношения:

где:

i — индекс источника выбросов;

r — индекс радионуклида;

 — годовая эффективная доза без учета рассеивания, создаваемая r-м радионуклидом, выбрасываемым в атмосферный воздух из i-го источника, Зв/год.

25. Значение годовой эффективной дозы без учета рассеивания, создаваемой r-м радионуклидом, выбрасываемым в атмосферный воздух из i-го источника, для всех радионуклидов, за исключением 3H и 14C, рекомендуется определять с помощью следующего соотношения:

где:

 — годовая эффективная доза внешнего облучения без учета рассеивания от облака, создаваемая r-м радионуклидом, выбрасываемым в атмосферу из i-го источника, Зв/год;

 — годовая эффективная доза внешнего облучения без учета рассеивания за счет радиоактивного загрязнения поверхности земли, создаваемая r-м радионуклидом, выбрасываемым в атмосферу из i-го источника, Зв/год;

 — годовая эффективная доза внутреннего облучения без учета рассеивания за счет ингаляции радионуклидов, создаваемая r-м радионуклидом, выбрасываемым в атмосферу из i-го источника, Зв/год;

 ‒ годовая эффективная доза внутреннего облучения без учета рассеивания за счет потребления загрязненных радионуклидами пищевых продуктов местного сельскохозяйственного производства, создаваемая r-м радионуклидом, выбрасываемым в атмосферу из i-го источника, Зв/год.

26. Для расчета годовых эффективных доз без учета рассеивания , , , , создаваемых выбросами i-го организованного источника, рекомендуется использовать соотношения (21)–(24):

где:

Qr,i — годовой выброс r-го радионуклида из i-го источника, Бк/год;

Wi — среднегодовой расход воздуха из i-го источника, м3/год;

 — коэффициент дозового преобразования при внешнем облучении человека от облака для радионуклида r, (Звм3)/(сБк);

 — коэффициент дозового преобразования при внешнем облучении человека от радиоактивно загрязненной поверхности без учета глубинного распределения для радионуклида r, (Звм2)/(сБк);

 — скорость сухого осаждения радионуклида r на подстилающую поверхность (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности), м/с;

 — постоянная радиоактивного распада радионуклида r, с–1;

 — постоянная спада мощности дозы -излучения от загрязненной поверхности земли за счет экранирования верхними слоями почвы, диффузии вглубь и выведения радионуклидов из нее за счет различных процессов, кроме радиоактивного распада, с–1 (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 1,2710–9 с–1);

 — интенсивность вдыхания для лиц возрастной группы, которая является критической по поступлению радионуклида r за счет ингаляции, м3/с;

 — коэффициент дозового преобразования при ингаляции радионуклида r, Зв/Бк;

Ir,f — годовое потребление продукта f лицом из возрастной группы, которая является критической по пероральному поступлению радионуклида r с пищевыми продуктами, кг/год;

αf — доля потребления продуктов местного сельскохозяйственного производства в общем потреблении продуктов (в случае отсутствия данных местных натурных исследований рекомендуется консервативно принимать равной единице; в случае отсутствия потребления населением сельскохозяйственной продукции, произведенной в районе влияния организации, осуществляющей выбросы, при условии, что это подтверждено официальными статистическими данными, данный параметр рекомендуется принимать равным нулю);

 — коэффициент дозового преобразования при пероральном поступлении радионуклида r, Зв/Бк;

 — коэффициент перехода «выпадение из атмосферы — поступление в продукт» радионуклида r в продукт питания f по воздушному пути, м2·год/кг;

 — коэффициент перехода «выпадение из атмосферы — поступление в продукт» радионуклида r в продукт питания f по корневому пути, м2·год/кг;

3,15·107 — число секунд в одном году.

27. Значение годовой эффективной дозы без учета рассеивания, создаваемой радионуклидом 3H, выбрасываемым в атмосферный воздух из i-го организованного источника, рекомендуется рассчитывать с помощью соотношения:

где:

 ‒ годовой выброс 3H из i-го источника, Бк/год;

Wi ‒ среднегодовой расход воздуха из i-го источника, м3/год;

– дозовый коэффициент для трития, значение которого рекомендуется принимать равным 2,6·10-8 (Зв·л)/(Бк·год);

H — абсолютная влажность воздуха, значение которой в случае отсутствия данных местных натурных исследований рекомендуется принимать равным 6∙10-3 л/м3.

28. Значение годовой эффективной дозы без учета рассеивания, создаваемой радионуклидом 14C, выбрасываемым в атмосферный воздух из i-го организованного источника, рекомендуется рассчитывать с помощью соотношения:

где:

 — годовой выброс 14С из i-го источника, Бк/год;

Wi ‒ среднегодовой расход воздуха из i-го источника, м3/год;

 — параметр, который рекомендуется принять равным 1,8·10–1 г/м3;

 — дозовый коэффициент для углерода, значение которого рекомендуется принимать равным 5,6·10–5 (Зв·г)/(Бк·год).

29. Значение фактического годового выброса r-го радионуклида из i-го организованного источника для проведения расчетов с помощью соотношений (21)–(26) рекомендуется определять с использованием рекомендаций руководства по безопасности при использовании атомной энергии «Рекомендации по методам и средствам контроля за выбросами радиоактивных веществ в атмосферный воздух» (РБ-135-17), утвержденного приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 августа 2017 г. № 347.

30. Для неорганизованных площадных источников расчет годовой эффективной дозы без учета рассеивания рекомендуется выполнять с помощью соотношений, аналогичных соотношениям (21)–(26), с использованием параметра., Бк/м3, характеризующего максимальную на множестве рассматриваемых румбов приземную активность r-го радионуклида в воздухе на краю площадного источника, вместо отношения Qr,i/Wi.

Величину приземной активности r-го радионуклида в воздухе на краю площадного источника рекомендуется определять путем произведения интенсивности выброса данного радионуклида, выраженной в Бк/с, на величину фактора разбавления на краю площадного источника, рассчитанную с помощью соотношения (6) приложения № 1 к настоящему Руководству по безопасности.

31. Для определения перечня радионуклидов в выбросах i-го источника, для которых в соответствии с пунктом 7 Методики должны быть установлены нормативы, рекомендуется использовать следующий алгоритм:

1) для каждого радионуклида, входящего в состав выброса из данного источника и включенного в Перечень загрязняющих веществ, в отношении которых применяются меры государственного регулирования в области охраны окружающей среды, утвержденный распоряжением Правительства Российской Федерации от 8 июля 2015 г. № 1316-р (далее — Перечень), определить вклад в годовую эффективную дозу, используя следующее соотношение:

где  — годовая эффективная доза без учета рассеивания, создаваемая r-м радионуклидом, выбрасываемым в атмосферный воздух из i-го источника, Зв/год;

2) произвести суммирование отношений доз в порядке убывания их значений до достижения суммой значения, большего или равного 0,99;

3) определить перечень радионуклидов, для которых должны быть установлены нормативы, по количеству отношений, вошедших в перечень тех, сумма которых больше или равна 0,99.

В случае если в выбросах из i-го источника присутствуют радионуклиды, не включенные в Перечень, при определении перечня радионуклидов в выбросах данного источника, для которых в соответствии с пунктом 7 Методики должны быть установлены нормативы, рекомендуется рассмотренный выше алгоритм распространить и на такие радионуклиды. При этом, в случае если реализация такого алгоритма приводит к тому, что ряд радионуклидов, входящих в Перечень, не входит в перечень тех, сумма вкладов которых в годовую эффективную дозу больше или равна 0,99, рекомендуется предусмотреть расчет нормативов предельно допустимых выбросов (далее — ПДВ) и для таких радионуклидов.

IV. Рекомендации по применению рассчитанных параметров для расчета нормативов предельно допустимых выбросов

32. Так как согласно пункту 7 Методики нормативы ПДВ устанавливаются исходя из непревышения выделенной организации части предела эффективной дозы (или пределов каждой из эквивалентных доз), рекомендуется их рассчитывать с использованием следующего соотношения:

где:

ПДВr,ieff — нормативы ПДВ, рассчитанные исходя из непревышения части предела годовой эффективной дозы;

ПДВr,ieq, кожа — нормативы ПДВ, рассчитанные исходя из непревышения части предела годовой эквивалентной дозы в коже;

ПДВr,ieq, хрусталик — нормативы ПДВ, рассчитанные исходя из непревышения части предела годовой эквивалентной дозы в хрусталике глаза;

ПДВr,ieq, кисти — нормативы ПДВ, рассчитанные исходя из непревышения части предела годовой эквивалентной дозы в кистях;

ПДВr,ieq, стопы — нормативы ПДВ, рассчитанные исходя из непревышения части предела годовой эквивалентной дозы в стопах.

33. Для расчета величин ПДВr,ieff и ПДВr,ieq,k рекомендуется использовать соотношения, приведенные в пунктах 34–37 настоящего Руководства по безопасности.

34. Величины ПДВr,ieff и ПДВr,ieq, k рекомендуется рассчитывать с помощью соотношений:

где:

 — относительный вклад каждого радионуклида r в общую активность его выброса из i-го источника, который рекомендуется рассчитывать по формуле (31):

 — часть предела эффективной дозы для населения, Зв/год;

k — индекс органа или ткани, принимающий значения: 1 — для кожи, 2 — для хрусталика глаза, 3 — для кистей, 4 — для стоп;

 — часть предела эквивалентной дозы в хрусталике глаза, коже, кистях и стопах соответственно, Зв/год, рассчитываемая (в случае если она не установлена органами, осуществляющими санитарно-эпидемиологический надзор) по формуле (32):

где:

ПД — предел годовой эффективной дозы для населения, Зв/год;

ПДk — предел годовой эквивалентной дозы в k-ом органе или ткани для населения, Зв/год;

xmax и ymax — декартовы координаты точки максимума годовой эффективной дозы, м;

xkmax и ykmax — декартовы координаты точек максимума эквивалентной дозы в хрусталике глаза, коже, кистях и стопах, м;

,  — функции перехода, связывающие активность выброса с годовой эффективной дозой облучения населения или эквивалентной дозой в k-ом органе или ткани, зависящие от декартовых координат и определенные соотношениями:

где:

 — оператор преобразования набора координат «расстояние от источника, направление» (x,n) в набор декартовых координат (x,y);

 — функция перехода, связывающая активность выбросов и создаваемую ими величину годовой эффективной дозы облучения населения, выраженная в полярных координатах, рекомендуемые методы расчета которой представлены в разделе II настоящего Руководства по безопасности, Зв/Бк;

 — функция перехода, связывающая активность выбросов и создаваемую ими величину годовой эквивалентной дозы облучения населения в k-ом органе или ткани, выраженная в полярных координатах, Зв/Бк.

35. Функционал  рекомендуется рассчитывать по формуле:

где:

 — дозовый коэффициент, предназначенный для пересчета единичной концентрации радионуклида r в приземном слое воздуха в мощность эквивалентной дозы в k-ом органе или ткани, Зв·м3/(Бк·с);

 — дозовый коэффициент, предназначенный для пересчета единичной поверхностной концентрации радионуклида r на поверхности земли в мощность эквивалентной дозы в k-ом органе или ткани, Зв·м2/(Бк·с);

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы для радионуклида r на расстоянии x от i-го организованного источника в n-ом румбе, с/м3;

 — среднегодовой метеорологический фактор разбавления в приземном слое атмосферы на расстоянии x от i-го неорганизованного площадного источника в n-ом румбе, с/м3;

 — среднегодовой метеорологический фактор сухого осаждения радионуклида r на подстилающую поверхность на расстоянии x от i-го источника в n-ом румбе, м–2;

 — среднегодовой метеорологический фактор влажного выведения радионуклида r на подстилающую поверхность на расстоянии x от i-го источника в n-ом румбе, м–2;

 — постоянная радиоактивного распада радионуклида r, с–1;

 — постоянная спада мощности дозы со временем от загрязненного слоя почвы за счет всех процессов, кроме радиоактивного распада, приводящих к выведению активности из этого слоя, с–1 (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 1,2710–9 с–1).

Рекомендуемые значения  и  для кожи приведены в таблице № 6 приложения № 2 к настоящему Руководству по безопасности.

Значения дозовых коэффициентов для хрусталика глаза рекомендуется консервативно принять равными 0,3 от значений соответствующих дозовых коэффициентов для кожи. Значения дозовых коэффициентов для кистей и стоп рекомендуется принимать равными значениям коэффициентов для кожи.

36. Для случая множественных удаленных друг от друга на значительные расстояния и отличающихся по своим характеристикам источников расчет нормативов ПДВ рекомендуется использовать следующие соотношения:

где:

Qr,i — величина годового выброса r-го радионуклида из i-го источника выброса, Бк/год;

 — часть предела эффективной дозы для населения, Зв/год;

Heffmax — максимальное значение годовой эффективной дозы, создаваемой всеми выбросами организации, Зв/год, определяемое следующим соотношением:

где:

(x, y) — координаты узла выбранной расчетной пространственной сетки в декартовой системе координат;

 — функция перехода, рассчитываемая с использованием соотношения (33) настоящего Руководства по безопасности;

maxx,y — символ, характеризующий максимальное значение расчетных значений функции перехода  по всем узлам с координатами (x, y) расчетной пространственной сетки.

37. Величины ПДВr,ieq, k рекомендуется оценивать с помощью соотношений, аналогичных (36) и (37), с использованием значений δk вместо δ, Heq, kmax вместо Heffmax и  вместо .

38. Проверку выполнения условия обеспечения сохранения благоприятных условий жизнедеятельности человека и устойчивого функционирования естественных экологических систем, природных и природно-антропогенных объектов, а также сохранения биологического видового разнообразия, требуемую положениями пункта 7 Методики, в части, касающейся соблюдения требований по ограничению содержания радионуклидов в поверхностном слое почвы, рекомендуется выполнять с помощью соотношения:

где:

ПДВr,i — значение предельно допустимого выброса r-го радионуклида из i-го источника, Бк/год;

УАНИr — параметр, рекомендуемые значения которого для различных радионуклидов приведены в таблицах № 7 и 8 приложения № 2 к настоящему Руководству по безопасности, Бк/кг;

 — среднегодовой метеорологический фактор сухого осаждения радионуклида r на подстилающую поверхность на расстоянии x от i-го источника выброса в n-ом румбе, м–2;

 — среднегодовой метеорологический фактор влажного выведения радионуклида r на подстилающую поверхность на расстоянии x от i-го источника выброса в n-ом румбе, м–2;

 — постоянная радиоактивного распада радионуклида r, год–1;

 — постоянная спада мощности дозы со временем от загрязненного слоя почвы за счет всех процессов, кроме радиоактивного распада, приводящих к выведению активности из этого слоя, год–1 (в случае отсутствия данных местных натурных исследований рекомендуется принимать равной 0,04 год–1);

ρ — поверхностная плотность корневого слоя почвы, кг/м2 (в случае отсутствия данных местных натурных исследований рекомендуется принимать в соответствии с таблицей № 3 приложения № 2 настоящего Руководства по безопасности).

В случае, если при проверке соблюдения требований по ограничению содержания радионуклидов в поверхностном слое почвы условие, указанное в соотношении (38), не выполняется, величины ПДВr,i уменьшаются до значений, при которых данное условие начнет выполняться.

39. Пример расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов, приведен в приложении № 4 к настоящему Руководству по безопасности.

Приложение № 1

к руководству по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух», утвержденному приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 августа 2021 г. № 288.

Рекомендуемые методы расчета фактора разбавления, факторов сухого осаждения и влажного выведения

1. Среднегодовой метеорологический фактор разбавления радионуклида r в приземном слое воздуха на расстоянии x от i-го организованного источника выбросов в n-ом румбе рекомендуется рассчитывать по формуле:

где:

j — номер градации категории устойчивости атмосферы, определяемый согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности;

k — номер градации модуля скорости ветра на высоте флюгера (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

n — номер румба;

N — число румбов;

x — расстояние от источника выбросов, м;

Uj,k — модуль скорости ветра на высоте выброса hs при скорости ветра на высоте флюгера из градации k для j-й категории устойчивости атмосферы, м/с (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — дисперсия струи по вертикали на расстоянии x от источника выбросов для j-й категории устойчивости атмосферы (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

n,j,k — повторяемость метеорологических условий, представляющая собой вероятность совместной реализации направления ветра в румбе n при категории устойчивости j и градации скорости ветра k;

hs,i — геометрическая высота i-го организованного источника, из которого осуществляется выброс, м;

hi,j,k (x) — высота подъема струи над устьем i-го организованного источника выбросов при скорости ветра на высоте флюгера из градации k для j-й категории устойчивости атмосферы за счет динамических и термических факторов, м (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — фактор истощения струи за счет радиоактивного распада радионуклида r, сухого осаждения и влажного выведения из атмосферы на подстилающую поверхность (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

Kb,i — доля выбросов, попадающая в зону аэродинамической тени за зданием при низком выбросе, для высоких источников принимаемая равной нулю (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — величина «виртуального» сдвига характеристик рассеяния доли выброса из i-го организованного источника, попадающей в зону аэродинамической тени, м (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности).

2. В случае, если отсутствуют данные о совместной реализации направления ветра в румбе n при категории устойчивости j и градации скорости ветра k, фактор разбавления для i-го организованного источника рекомендуется рассчитывать следующим образом:

где:

j — номер категории устойчивости атмосферы;

n — номер румба;

N — число румбов;

x — расстояние от источника выбросов, м;

 — повторяемость направлений ветра;

 — среднегодовая скорость ветра на высоте выброса, м/с;

 — дисперсия струи по вертикали на расстоянии x от источника выбросов для j-й категории устойчивости атмосферы (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

hs,i — геометрическая высота i-го организованного источника, из которого осуществляется выброс, м;

hi,j (x) — высота подъема струи над устьем i-го организованного источника выбросов при скорости ветра на высоте флюгера для j-й категории устойчивости атмосферы за счет динамических и термических факторов, м (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — фактор истощения струи за счет радиоактивного распада радионуклида r, сухого осаждения и влажного выведения из атмосферы на подстилающую поверхность (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

Kb,i — доля выбросов, попадающая в зону аэродинамической тени за зданием при низком выбросе, для высоких источников принимаемая равной нулю (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

– величина «виртуального» сдвига, м (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности).

3. Среднегодовой метеорологический фактор сухого осаждения радионуклида r на подстилающую поверхность на расстоянии x от i-го организованного источника выбросов в n-ом румбе рекомендуется рассчитывать по формуле:

где:

 — скорость сухого осаждения радионуклида r на подстилающую поверхность (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности), м/с;

 — среднегодовой метеорологический фактор разбавления для i-го организованного источника выбросов, с/м3.

4. Среднегодовой метеорологический фактор влажного выведения радионуклида r из облака на подстилающую поверхность на расстоянии x от i-го организованного источника выбросов в n-ом румбе рекомендуется рассчитывать по формуле:

где:

 — постоянная вымывания радионуклида r из атмосферы осадками, усредненная за год с учетом типа и продолжительности осадков в течение года, с–1 (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — интеграл по вертикальной координате z от зависящего от высоты над поверхностью земли среднегодового фактора разбавления, который для i-го организованного источника выбросов рекомендуется определять по следующей формуле:

где:

j — номер градации категории устойчивости атмосферы, (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

k — номер градации модуля скорости ветра на высоте флюгера (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

n — номер румба;

N — число румбов;

x — расстояние от источника выбросов, м;

Uj,k — модуль скорости ветра на высоте выброса hs,i при скорости ветра на высоте флюгера из градации k для j-й категории устойчивости атмосферы, м/с (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — дисперсия струи по вертикали на расстоянии x от источника выбросов для j-й категории устойчивости атмосферы (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

n,j,k — повторяемость метеорологических условий, представляющая собой вероятность совместной реализации направления ветра в румбе n при категории устойчивости j и градации скорости ветра k (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — фактор истощения струи за счет радиоактивного распада радионуклида r, сухого осаждения и влажного выведения из атмосферы на подстилающую поверхность (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности).

5. Среднегодовой метеорологический фактор разбавления на расстоянии x от i-го неорганизованного площадного источника выброса в n-ом румбе, с/м3, рекомендуется определять следующим образом:

где:

S — площадь поверхности площадного источника, м2;

a — половина длины стороны площадного источника, м;

Uk — скорость ветра на высоте флюгера, м/с;

 — расстояние от центра площадного источника вдоль направления ветра, м;

 — дисперсия струи по вертикали на расстоянии x от источника выбросов для j-й категории устойчивости атмосферы (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

 — переменная интегрирования, м;

Pj(x) — функция, определяемая следующим соотношением:

где:

H — высота слоя перемешивания, м, значение которой рекомендуется принять равной , где  — параметр, рекомендуемые значения которого для различных категорий устойчивости атмосферы j приведены в приложении № 3 к настоящему Руководству по безопасности;

Z — высота над поверхностью земли, значение которой рекомендуется принять равной 1 м;

l — переменная суммирования.

6. Среднегодовой метеорологический фактор влажного выведения радионуклида r из облака на подстилающую поверхность на расстоянии x от i-го неорганизованного площадного источника выброса в n-ом румбе рекомендуется рассчитывать по формуле:

где:

 — постоянная вымывания примеси из атмосферы осадками, усредненная за год с учетом типа и продолжительности осадков в течение года, с–1 (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

Uk — скорость ветра на высоте флюгера, м/с;

n,j,k — повторяемость метеорологических условий, представляющая собой вероятность совместной реализации направления ветра в румбе n при категории устойчивости j и градации скорости ветра k;

x — расстояние от источника выбросов, м;

 — дисперсия струи в горизонтальном направлении на расстоянии x от источника выбросов для j-й категории устойчивости атмосферы (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности);

j — номер градации категории устойчивости атмосферы, определяемый согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности;

k — номер градации модуля скорости ветра на высоте флюгера, определяемый согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности;

n — номер румба.

7. Среднегодовой метеорологический фактор сухого осаждения радионуклида r на подстилающую поверхность на расстоянии x от i-го неорганизованного площадного источника выброса в n-ом румбе рекомендуется рассчитывать по формуле:

где:

 — скорость сухого осаждения радионуклида r на подстилающую поверхность (определяется согласно рекомендациям приложения № 3 к настоящему Руководству по безопасности), м/с;

 — среднегодовой метеорологический фактор разбавления для i-го неорганизованного площадного источника, значение которого рекомендуется рассчитывать с помощью соотношения (6) данного приложения к настоящему Руководству по безопасности, с/м3.

8. Рекомендации по учету начального разбавления выброса и учет влияния зданий при выбросах из низких источников приведены в приложении № 3 к настоящему Руководству по безопасности.

Приложение № 2

к руководству по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух», утвержденному приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 августа 2021 г. № 288.

Рекомендуемые значения параметров, используемых при расчете доз облучения человека

Для расчета функций перехода рекомендуется использовать данные из таблиц № 1–6 настоящего приложения.

Таблица № 1. Рекомендуемые значения дозовых коэффициентов  и *

225Ac

8,06∙10–16

1,09∙10-17

227Ac

8,16∙10–18

9,54∙10–20

228Ac

5,26∙10–14

7,37∙10–16

110Ag

7,11∙10–15

2,23∙10–16

110mAg

1,64∙10–13

2,22∙10–15

241Am

1,01∙10–15

1,55∙10–17

243Am

2,70∙10–15

4,08∙10–17

41Ar

7,85∙10–14

–**

217At

1,43∙10–17

1,97∙10–19

218At

4,83∙10–18

1,83∙10–19

198Au

2,47∙10–14

3,68∙10–16

140Ba

1,14∙10–14

1,78∙10–16

210Bi

1,26∙10–15

5,09∙10–17

211Bi

2,78∙10–15

3,88∙10–17

212Bi

8,10∙10–15

1,64∙10–16

213Bi

8,96∙10–15

1,58∙10–16

214Bi

9,14∙10–14

1,25∙10–15

45Ca

1,16∙10–16

1,68∙10–18

47Ca

6,42∙10–14

8,59∙10–16

141Ce

4,66∙10–15

6,22∙10–17

144Ce

1,17∙10–15

1,59∙10–17

36Cl

7,88∙10–16

2,10∙10–17

242Cm

1,11∙10–17

7,55∙10–20

243Cm

7,51∙10–15

1,00∙10-16

244Cm

1,04∙10–17

7,55∙10–20

57Co

7,16∙10–15

9,34∙10–17

58Co

5,78∙10–14

7,95∙10–16

60Co

1,50∙10–13

1,95∙10–15

51Cr

1,89∙10–15

2,60∙10–15

134Cs

9,25∙10–14

1,28∙10–15

135Cs

1,47∙10–16

2,09∙10–18

137Cs/137mBa

3,52∙10–14

5,01∙10–16

138Cs

1,48∙10–13

2,01∙10–15

169Er

1,80∙10–16

2,51∙10–18

152Eu

6,96∙10–14

9,34∙10–16

154Eu

7,49∙10–14

1,01∙10-15

155Eu

3,27∙10–15

4,60∙10–17

59Fe

7,13∙10–14

9,34∙10–16

221Fr

1,72∙10–15

2,33∙10–17

223Fr

3,86∙10–15

8,11∙10–17

67Ga

9,11∙10–15

1,24∙10–16

197Hg

3,35∙10–15

5,10∙10–17

123I

9,20∙10–15

1,23∙10–16

129I

6,18∙10–16

1,08∙10–17

131I

2,31∙10–14

3,23∙10–16

132I

1,36∙10–13

1,91∙10–15

133I

3,76∙10–14

5,63∙10–16

134I

1,57∙10–13

2,17∙10–15

135I

9,61∙10–14

1,27∙10–15

111In

2,32∙10–14

3,11∙10–16

192Ir

4,87∙10–14

6,81∙10–16

42K

2,37∙10–14

4,44∙10–16

85Kr

8,28∙10–16

–**

85mKr

9,94∙10–15

–**

87Kr

5,43∙10–14

–**

88Kr

1,20∙10–13

–**

140La

1,41∙10–13

1,86∙10–15

54Mn

4,96∙10–14

6,77∙10–16

99Mo

1,00∙10–14

1,73∙10–16

22Na

1,31∙10–13

1,77∙10–15

24Na

2,54∙10–13

3,02∙10–15

95Nb

4,54∙10–14

6,25∙10–16

237Np

1,29∙10–15

1,79∙10–17

239Np

1,06∙10–14

1,42∙10–16

32P

2,64∙10–15

1,18∙10–16

231Pa

2,02∙10–15

2,75∙10–17

233Pa

1,28∙10–14

1,75∙10–16

234Pa

8,71∙10–14

1,18∙10–15

234mPa

4,25∙10–15

1,50∙10–16

209Pb

5,04∙10–16

9,64∙10–18

210Pb

8,57∙10–17

1,25∙10–18

211Pb

5,35∙10–15

1,19∙10–16

212Pb

8,52∙10–15

1,17∙10–16

214Pb

1,54∙10–14

2,19∙10–16

147Pm

8,02∙10–17

1,20∙10–18

210Po

5,77∙10–19

7,92∙10–21

211Po

4,85∙10–16

6,68∙10–18

214Po

4,93∙10–18

6,76∙10–20

215Po

1,04∙10–17

1,47∙10–19

216Po

9,09∙10–19

1,25∙10–20

218Po

2,06∙10–20

3,01∙10–22

144Pr

7,21∙10–15

2,23∙10–16

144mPr

4,26∙10–16

6,96∙10–18

238Pu

1,00∙10–17

5,85∙10–20

239Pu

7,55∙10–18

7,12∙10–20

240Pu

9,65∙10–18

5,82∙10–20

241Pu

1,57∙10–19

2,35∙10–21

223Ra

7,94∙10–15

1,09∙10–16

224Ra

6,15∙10–16

8,32∙10–18

225Ra

5,64∙10–16

8,91∙10–18

226Ra

4,31∙10–16

5,76∙10–18

87Rb

2,15∙10–16

2,98∙10–18

88Rb

5,06∙10–14

7,94∙10–16

89Rb

1,40∙10–13

1,85∙10–15

103mRh

1,44∙10–17

1,39∙10–19

106Rh

1,89∙10–14

4,00∙10–16

218Rn

4,48∙10–17

6,29∙10–19

219Rn

3,46∙10–15

4,79∙10–17

220Rn

3,71∙10–17

5,25∙10–19

222Rn

2,30∙10–17

3,25∙10–19

103Ru

2,94∙10–14

4,16∙10–16

106Ru

1,25∙10–18

2,16∙10–20

35S

4,99∙10–17

7,87∙10–19

122Sb

2,84∙10–14

4,58∙10–16

124Sb

1,12∙10–13

1,50∙10–15

125Sb

2,54∙10–14

3,58∙10–16

47Sc

6,80∙10–15

8,96∙10–17

75Se

2,28∙10–14

3,08∙10–16

89Sr

2,14∙10–15

9,53∙10–17

90Sr

4,93∙10–16

7,96∙10–18

99Tc

1,80∙10–16

2,52∙10–18

99mTc

7,41∙10–15

9,66∙10–17

123Te

5,73∙10–19

9,41∙10–21

123mTe

8,15∙10–15

1,07∙10–16

125mTe

6,91∙10–16

1,16∙10–17

227Th

7,19∙10–15

9,82∙10–17

228Th

1,20∙10–16

1,59∙10–18

229Th

4,78∙10–15

6,50∙10–17

230Th

2,43∙10–17

3,01∙10–19

231Th

8,09∙10–16

1,10∙10–17

232Th

1,40∙10–17

1,59∙10–19

234Th

5,16∙10–16

7,36∙10–18

201Tl

4,55∙10–15

6,67∙10–17

206Tl

1,93∙10–15

8,51∙10–17

207Tl

1,87∙10–15

7,73∙10–17

208Tl

2,07∙10–13

2,51∙10–15

209Tl

1,31∙10–13

1,77∙10–15

232U

2,03∙10–17

2,05∙10–19

233U

1,75∙10–17

2,03∙10–19

234U

1,34∙10–17

1,15∙10-19

235U

9,57∙10–15

1,27∙10–16

236U

9,60∙10–18

6,79∙10–20

237U

7,65∙10–15

1,04∙10-16

238U

7,88∙10–18

5,70∙10–20

127Xe

1,56∙10–14

–**

131mXe

5,95∙10–16

–**

133Xe

2,18∙10–15

–**

133mXe

1,85∙10–15

–**

135Xe

1,56∙10–14

–**

135mXe

2,50∙10–14

–**

138Xe

7,03∙10–14

–**

90Y

3,91∙10–15

1,58∙10–16

65Zn

3,46∙10–14

4,57∙10–16

95Zr

4,36∙10–14

6,03∙10–16

* Значения коэффициентов приняты в соответствии с EPA 402-R-19-002 Federal Guidance Report No. 15. External Exposure to Radionuclides in Air, Water and Soil. — U.S. Environmental Protection Agency, 2019.

** Данный путь облучения не учитывается для радионуклидов группы инертных радиоактивных газов (далее — ИРГ).

Таблица № 2. Рекомендуемые значения интенсивностей вдыхания для различных возрастных групп населения, м3/с

Возрастная группа, g

2

3

4

5

6

Возраст

1–2 года

2–7 лет

7–12 лет

12–17 лет

>17

U rI, м3/с

6,032·10–5

1,016·10–4

1,651·10–4

2,317·10–4

2,571·10–4

Таблица № 3. Рекомендуемые значения поверхностной плотности корневого слоя почвы ρ*, кг/м2

Вид использования почвы

Тип почвы

Торфянистые почвы

Неторфянистые виды почв

Выращивание сельскохозяйственных культур

100

260

Выпас сельскохозяйственных животных

50

130

* Значения коэффициентов приняты в соответствии с Generic Models for use in Assessing the Impact of Discharges of Radioactive Substances to the Environment / Safety Reports. — Series No. 19.–Vienna: IAEA, 2000.

Таблица № 4. Рекомендуемые значения параметров Fνr, Fν1r, Fmмолоко, r, Ffмясо, r *

Ac

0,001

2·10–6

2·10–5

0,1

Ag

0,01

1·10–4

0,006

0,1

Am

0,002

2·10–5

1·10–4

0,1

At

0,2

0,01

0,01

0,9

Au

0,1

1·10–5

0,005

0,4

Ba

0,05

0,005

0,002

0,1

Bi

0,1

0,001

0,002

0,5

Ce

0,05

3·10–4

2·10–4

0,1

Cm

0,001

2·10–6

2·10–5

0,1

Co

0,08

0,01

0,07

2

Cr

0,001

2·10–4

0,09

0,1

Cs

0,3

0,01

0,05

20

Eu

0,002

6·10–5

0,002

0,1

Fe

0,001

3·10–4

0,05

0,1

Ga

0,003

1·10–5

3·10–4

0,1

Hg

0,3

5·10–4

0,01

3

I

0,02

0,01

0,05

0,1

In

0,003

2·10–4

0,004

0,1

Mn

0,3

3·10–4

7·10–4

10

Mo

0,2

0,005

0,01

1

Na

0,05

0,25

0,8

0,6

Nb

0,01

4·10–6

3·10–6

0,2

Ni

0,3

0,2

0,05

1

Np

0,04

5·10–5

0,01

0,5

P

1

0,02

0,05

10

Pa

0,01

5·10–6

5·10–6

0,1

Pb

0,02

3·10–4

7·10–4

0,1

Pm

0,002

6·10–5

0,002

0,1

Po

0,002

0,003

0,005

0,1

Pu

0,001

3·10–6

2·10–4

0,1

Ra

0,04

0,001

0,005

0,4

Rb

0,2

0,1

0,03

2

Rh

0,2

5·10–4

0,002

2

Ru

0,05

3·10–5

0,05

0,2

S

0,6

0,02

0,2

6

Sb

0,001

2,5·10–4

0,005

0,1

Se

0,1

0,001

0,1

1

Sr

0,3

0,003

0,01

10

Tc

5

0,001

0,001

80

Te

1

0,005

0,07

10

Th

0,001

5·10–6

1·10–4

0,1

Tl

2

0,003

0,02

2

U

0,01

6·10–4

0,003

0,2

Y

0,003

6·10–5

0,01

0,1

Zn

2

0,01

0,2

2

Zr

0,001

6·10–6

1·10–5

0,1

* Значения коэффициентов приняты в соответствии с Generic Models for use in Assessing the Impact of Discharges of Radioactive Substances to the Environment / Safety Reports. — Series No. 19. — Vienna: IAEA, 2000.

Таблица № 5. Рекомендуемые значения суточных энергетических затрат для лиц из различных возрастных групп, ккал/сут

Возрастная группа (g)

2

3

4

5

6

Возраст

1–2 года

2–7 лет

7–12 лет

12–17 лет

>17

Энергетические затраты, ккал/сут

1 400

2 000

2 600

3 100

2 900

Таблица № 6. Рекомендуемые значения дозовых коэффициентов  и *

225Ac

9,40∙10–16

3,08∙10–17

227Ac

1,10∙10–17

7,43∙10–19

228Ac

7,88∙10–14

4,75∙10–15

110Ag

8,22∙10–14

1,27∙10–14

110mAg

1,57∙10–13

3,22∙10–15

241Am

1,28∙10–15

8,32∙10–17

243Am

2,75∙10–15

7,60∙10–17

41Ar

1,01∙10–13

–**

217At

1,86∙10–17

4,11∙10–19

218At

2,12∙10–16

2,32∙10–17

198Au

4,08∙10–14

2,53∙10–15

140Ba

2,52∙10–14

1,95∙10–15

210Bi

2,30∙10–14

3,42∙10–15

211Bi

3,07∙10–15

5,55∙10–17

212Bi

4,05∙10–14

5,35∙10–15

213Bi

3,39∙10–14

4,23∙10–15

214Bi

1,28∙10–13

8,48∙10–15

45Ca

1,46∙10–15

1,61∙10–19

47Ca

8,02∙10–14

3,42∙10–15

141Ce

1,02∙10–14

1,32∙10–16

144Ce

2,93∙10–15

2,61∙10–17

36Cl

1,47∙10–14

1,06∙10–15

242Cm

4,29∙10–17

9,38∙10–18

243Cm

9,79∙10–15

1,90∙10–16

244Cm

3,91∙10–17

8,70∙10–18

57Co

6,63∙10–15

1,38∙10–16

58Co

5,58∙10–14

1,14∙10–15

60Co

1,45∙10–13

2,76∙10–15

51Cr

1,75∙10–15

3,68∙10–17

134Cs

9,45∙10–14

2,17∙10–15

135Cs

9,06∙10–16

1,27∙10–19

137Cs/137mBa

3,73∙10–14

1,65∙10–15

138Cs

2,17∙10–13

1,52∙10–14

169Er

2,83∙10–15

2,46∙10–19

152Eu

6,90∙10–14

1,75∙10–15

154Eu

8,29∙10–14

2,91∙10–15

155Eu

3,39∙10–15

7,04∙10–17

59Fe

7,13∙10–14

1,34∙10–15

221Fr

2,02∙10–15

3,67∙10–17

223Fr

2,30∙10–14

2,72∙10–15

67Ga

8,50∙10–15

1,74∙10–16

197Hg

3,35∙10–15

9,10∙10–17

123I

9,40∙10–15

2,33∙10–16

129I

1,10∙10–15

5,80∙10–17

131I

2,98∙10–14

6,43∙10–16

132I

1,58∙10–13

7,54∙10–15

133I

5,83∙10–14

4,55∙10–15

134I

1,87∙10–13

9,85∙10–15

135I

1,11∙10–13

4,83∙10–15

111In

2,29∙10–14

5,09∙10–16

192Ir

5,53∙10–14

1,21∙10–15

42K

1,15∙10–13

1,41∙10–14

85Kr

1,32∙10–14

–**

85mKr

2,24∙10–14

–**

87Kr

1,37∙10–13

–**

88Kr

1,35∙10–13

–**

140La

1,66∙10–13

8,24∙10–15

54Mn

4,67∙10–14

9,65∙10–16

99Mo

3,14∙10–14

3,76∙10–15

22Na

1,33∙10–13

2,60∙10–15

24Na

2,75∙10–13

1,03∙10–14

95Nb

4,30∙10–14

9,05∙10–16

237Np

1,54∙10–15

8,36∙10–17

239Np

1,60∙10–14

2,63∙10–16

32P

4,49∙10–14

8,26∙10–15

231Pa

2,44∙10–15

1,07∙10–16

233Pa

1,66∙10–14

2,70∙10–16

234Pa

1,24∙10–13

3,89∙10–15

234mPa

5,48∙10–14

9,39∙10–15

209Pb

9,35∙10–15

2,94∙10–16

210Pb

1,28∙10–16

1,98∙10–17

211Pb

3,06∙10–14

4,64∙10–15

212Pb

1,35∙10–14

1,88∙10–16

214Pb

2,77∙10–14

9,10∙10–16

147Pm

8,11∙10–16

1,20∙10–19

210Po

4,81∙10–19

1,11∙10–20

211Po

4,47∙10–16

1,12∙10–17

214Po

4,71∙10–18

1,09∙10–19

215Po

1,01∙10–17

2,15∙10–19

216Po

9,57∙10–19

2,20∙10–20

218Po

7,56∙10–19

1,17∙10–20

144Pr

8,43∙10–14

1,27∙10–14

144mPr

5,08∙10–16

2,67∙10–17

238Pu

4,09∙10–17

9,64∙10–18

239Pu

1,86∙10–17

3,67∙10–18

240Pu

3,92∙10–17

9,18∙10–18

241Pu

1,17∙10–19

7,06∙10–21

223Ra

8,87∙10–15

1,67∙10–16

224Ra

6,35∙10–16

1,16∙10–17

225Ra

3,01∙10–15

3,25∙10–17

226Ra

4,79∙10–16

8,12∙10–18

87Rb

3,15∙10–15

2,73∙10–19

88Rb

1,83∙10–13

1,67∙10–14

89Rb

1,87∙10–13

1,21∙10–14

103mRh

4,49∙10–17

6,88∙10–18

106Rh

1,09∙10–13

1,42∙10–14

218Rn

4,30∙10–17

1,05∙10–18

219Rn

3,38∙10–15

6,64∙10–17

220Rn

2,20∙10–17

5,21∙10–19

222Rn

2,28∙10–17

5,20∙10–19

103Ru

2,77∙10–14

6,16∙10–16

106Ru

1,09∙10–13

1,42∙10–14

35S

2,92∙10–16

7,54∙10–20

122Sb

6,03∙10–14

6,72∙10–15

124Sb

1,26∙10–13

5,20∙10–15

125Sb

2,65∙10–14

5,97∙10–16

47Sc

1,28∙10–14

1,95∙10–16

75Se

2,16∙10–14

4,76∙10–16

89Sr

3,69∙10–14

6,66∙10–15

90Sr

9,20∙10–15

1,40∙10–16

99Tc

2,74∙10–15

2,43∙10–19

99mTc

7,14∙10–15

1,44∙10–16

123Te

6,32∙10–16

5,71∙10–17

123mTe

8,48∙10–15

1,87∙10–16

125mTe

1,94∙10–15

9,45∙10–17

227Th

6,50∙10–15

1,56∙10–16

228Th

1,50∙10–16

9,74∙10–18

229Th

5,41∙10–15

1,57∙10–16

230Th

4,51∙10–17

7,17∙10–18

231Th

2,52∙10–15

8,58∙10–17

232Th

3,44∙10–17

6,86∙10–18

234Th

7,50∙10–16

1,72∙10–17

201Tl

4,89∙10–15

1,15∙10–16

206Tl

3,36∙10–14

5,89∙10–15

207Tl

3,06∙10–14

5,21∙10–15

208Tl

2,34∙10–13

9,77∙10–15

209Tl

1,59∙10–13

9,87∙10–15

232U

5,92∙10–17

1,10∙10–17

233U

4,57∙10–17

5,94∙10–18

234U

4,25∙10–17

9,09∙10–18

235U

8,64∙10–15

1,94∙10–16

236U

3,57∙10–17

8,45∙10–18

237U

9,97∙10–15

2,07∙10–16

238U

2,91∙10–17

7,42∙10–18

127Xe

1,57∙10–14

–**

131mXe

4,82∙10–15

–**

133Xe

4,97∙10–15

–**

133mXe

1,04∙10–14

–**

135Xe

3,12∙10–14

–**

135mXe

2,97∙10–14

–**

138Xe

1,07∙10–13

–**

90Y

6,24∙10–14

1,05∙10–14

65Zn

3,29∙10–14

6,52∙10–16

95Zr

4,50∙10–14

8,91∙10–16

* Значения коэффициентов приняты в соответствии с NUREG/CR-7166 Radiological Toolbox User’s Guide. — Office of Nuclear Regulatory Research, 2013.

** Данный путь облучения не учитывается для радионуклидов группы ИРГ.

Таблица № 7. Значения УАНИ, Бк/кг*, **, ***

110mAg****

102

241Am

102

243Am****

102

198Au

104

140Ba

103

45Ca

105

47Ca

104

141Ce

105

144Ce****

104

36Cl

103

242Cm

104

243Cm

103

244Cm

103

57Co

103

58Co

103

60Co

102

51Cr

105

134Cs

102

135Cs

105

137Cs****

102

138Cs

104

169Er

106

152Eu

102

154Eu

102

155Eu

103

59Fe

103

197Hg

105

123I

105

129I

101

131I

104

132I

104

133I

104

134I

104

135I

104

111In

104

192Ir

103

42K

105

140La

103

54Mn

102

99Mo****

104

c22Na

102

24Na

103

95Nb

103

237Np****

103

239Np

105

32P

106

233Pa

104

147Pm

106

238Pu

102

239Pu

102

240Pu

102

241Pu

104

225Ra

104

103mRh

108

103Ru****

103

106Ru****

102

35S

105

122Sb

104

124Sb

103

125Sb****

102

47Sc

105

75Se

103

89Sr

106

90Sr****

103

99Tc

103

99mTc

105

123mTe

103

125mTe

106

229Th

102

201Tl

105

232U****

102

233U

103

236U

104

237U

105

90Y

106

65Zn

102

95Zr****

103

* Для радионуклидов, за исключением изотопов урана: 234U, 235U, 238U.

** Значения коэффициентов приняты в соответствии с Radiation Protection and Safety of Radiation Sources: International Basic Safety Standards // General Safety Requirements Part 3. — IAEA, 2014.

*** В случае необходимости использования в расчетах величин УАНИ для радионуклидов, отсутствующих в таблице, рекомендуется принимать их значения в соответствии с таблицей I.1 Radiation Protection and Safety of Radiation Sources: International Basic Safety Standards // General Safety Requirements Part 3. — IAEA, 2014.

**** Значения УАНИ для данных радионуклидов приведены с учетом их дочерних продуктов распада:

110mAg:

243Am:

144Ce:

137Cs:

99Mo:

237Np:

103Ru:

106Ru:

125Sb:

90Sr:

232U:

95Zr:

110Ag

239Np

144Pr,

137mBa

99mTc

233Pa

103mRh

106Rh

125mSb

90Y

228Th,

95Nb.

144mPr

224Ra,

220Rn,

216Po,

 212Pb,

212Bi,

208Tl

Таблица № 8. Значения УАНИ для 234U, 235U, 238U, Бк/кг*

Радионуклид

УАНИ, Бк/кг

234U

104

103***

235U

104**

103***

238U

104**

103***

* Значения коэффициентов приняты в соответствии с Radiation Protection and Safety of Radiation Sources: International Basic Safety Standards // General Safety Requirements Part 3. — IAEA, 2014.

** Для изотопов урана, находящихся в равновесии со следующими дочерними продуктами распада:

235U:

238U:

231Th

234Th,

234mPa.

*** Для изотопов урана, находящихся в равновесии со своими дочерними продуктами распада:

234U:

235U:

238U:

230Th, 226Ra, 222Rn,

231Th, 231Pa, 227Ac,

234Th, 234mPa, 234Pa,

218Po, 214Pb, 218At,

227Th, 223Fr, 223Ra,

234U, 230Th, 226Ra,

214Bi, 218Rn, 214Po,

219Rn, 219At, 215Bi,

222Rn, 218Po, 214Pb,

210Tl, 210Pb, 210Bi,

215Po, 211Pb, 211Bi,

218At, 214Bi, 218Rn,

206Hg, 210Po, 206Tl

207Tl, 211Po

214Po, 210Tl, 210Pb,

210Pb, 210Bi, 206Hg,

210Po, 206Tl».

Приложение № 3

к руководству по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух», утвержденному приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 августа 2021 г. № 288.

Рекомендации по определению значений параметров, входящих в состав формул для расчета факторов разбавления, факторов сухого осаждения и влажного выведения

1. Расчет вертикальной дисперсии струи примеси для всех типов подстилающей поверхности, кроме типа «скошенная и низкая трава до 15 см», рекомендуется выполнять с использованием параметризации Смита-Хоскера по следующему соотношению:

где f(z0,x) и gj(x) рекомендуется определять по приведенным ниже формулам:

Рекомендуемые значения параметров , используемых при расчетах , в зависимости от категории устойчивости атмосферы приведены в таблице № 9 настоящего приложения. Рекомендуемые значения параметров , используемых при расчетах , в зависимости от коэффициента шероховатости z0 приведены в таблице № 10 настоящего приложения. Рекомендуемые значения верхней границы  для различных категорий устойчивости атмосферы приведены в таблице № 11 настоящего приложения. Рекомендуемые значения коэффициента шероховатости z0 для различных типов подстилающей поверхности приведены в таблице № 12 настоящего приложения.

Для типа подстилающей поверхности «Луг, скошенные и пахотные угодья» рекомендуется для вертикальной дисперсии использовать формулы Бриггса, а для учета ограниченности вертикальной дисперсии использовать значения  из таблицы № 11 настоящего приложения:

для категории A:

для категории B:

для категории C:

для категории D:

для категории E:

для категории F:

для категории G:

Таблица № 9. Рекомендуемые значения параметров, используемых при расчетах , в зависимости от категории устойчивости атмосферы*

Категория устойчивости

A

0,112

5,38·10-4

1,06

0,815

B

0,130

6,52·10-4

0,950

0,755

C

0,112

9,05·10-4

0,920

0,718

D

0,098

1,35·10-3

0,889

0,688

E

0,080

1,58·10-3

0,892

0,686

F

0,0609

1,96·10-3

0,895

0,684

G

0,0638

1,36·10-3

0,783

0,672

Таблица № 10. Рекомендуемые значения параметров, используемых при расчетах , в зависимости от коэффициента шероховатости z0*

0,01

1,56

0,0480

6,25·10-4

0,45

0,04

2,02

0,0269

7,76·10-4

0,37

0,1

2,72

0

0

0

0,4

5,16

-0,098

1,86∙101

-0,225

1,0

7,37

-0,0957

4,29∙103

-0,60

Таблица № 11. Рекомендуемые значения верхней границы для различных категорий устойчивости атмосферы

Категория устойчивости

A

B

C

D

E

F

G

, м

1600

1200

800

600

240

160

80

Таблица № 12. Рекомендуемые значения коэффициента шероховатости z0 для различных типов подстилающей поверхности

Тип подстилающей поверхности

, м

Водная поверхность

0,01

Неоднородная поверхность с чередующимися участками травы, кустарниками и т. п.

0,3

Сельская застройка

0,4

Парк, лес высотой до 10 м

0,8

Городские постройки

1,0

2. Вычисление модуля скорости ветра на высоте выброса рекомендуется производить по следующему соотношению:

где:

 — модуль приземной скорости ветра из градации по скоростям ветра k, м/с;

h — высота выброса, м;

 — высота флюгера (рекомендуется принимать равной 10 м);

 — безразмерный параметр, зависящий от категории устойчивости атмосферы и коэффициента мезомасштабной шероховатости  подстилающей поверхности.

Рекомендуемые значения εj (z0), используемого для расчета изменения скорости ветра с высотой, приведены в таблице № 13 настоящего приложения.

Таблица № 13. Рекомендуемые значения параметра εj (z0), используемого для расчета изменения скорости ветра с высотой

Категория устойчивости

,  = 1 см

,  = 10 см

,  = 40 см

,  = 100 см

A

0,05

0,08

0,11

0,16

B

0,06

0,09

0,13

0,17

C

0,06

0,11

0,16

0,20

D

0,12

0,16

0,22

0,27

E

0,22

0,22

0,27

0,31

F

0,34

0,34

0,39

0,42

G

0,52

0,52

0,57

0,60

3. Для вычисления распределения повторяемостей ωn,j,k по категориям устойчивости j, направлениям ветра n и группам скоростей ветра рекомендуется использовать данные, предоставленные метеостанциями, расположенными в районе расположения источника выброса.

4. Поскольку в штилевых условиях (k=1) направление ветра не определено, для штилей рекомендуется число наблюдений распределять по секторам направления ветра пропорционально частоте его распределения при слабом ветре (k=2).

5. Траекторию подъема струи Δhj,k(x) для всех погодных условий рекомендуется вычислять по формулам Неттервилла:

для категории D (безразличной стратификации атмосферы):

для категорий A, B и C (условий неустойчивости):

для категорий E, F и G (устойчивых условий):

где:

x — расстояние от основания трубы, м;

 — время движения облака по ветру до расстояния x, с;

 — скорость ветра на высоте выброса, м/с;

β — безразмерная константа переноса;

f=0,7·10-2 — характерная частота спектра турбулентности при нейтральной атмосфере, с-1;

 — параметр устойчивости атмосферы, с-1;

T0 — абсолютная температура атмосферного воздуха, К;

 — градиент потенциальной температуры (разница измеренного и адиабатического градиента температуры), К/м;

 — начальный радиус струи с поправкой Ханны, м;

w0 — скорость выбрасываемой газовоздушной смеси, м/с;

d — диаметр устья трубы, м;

 — величина, пропорциональная потоку кинетической энергии истекающей струи выброса, м4/с2;

 — величина, пропорциональная потоку сил плавучести, м4/с3;

g = 9,8 — ускорение свободного падения, м/с2;

 — разность температур выбрасываемого T и атмосферного Т0 воздуха, К.

Рекомендуемые значения параметров s и β для различных категорий устойчивости приведены в таблице № 14.

Таблица № 14. Рекомендуемые значения параметров s и β для различных категорий устойчивости

Категория устойчивости атмосферы

А

В

С

D

E

F

G

s, c-1

0,02

0,017

0,015

0,00

0,023

0,033

0,038

β

0,25

0,35

0,45

0,45

0,25

0,25

0,25

6. Рекомендуемые значения скоростей сухого осаждения радионуклидов из атмосферы на подстилающую поверхность приведены в таблице № 15 настоящего приложения.

Таблица № 15. Рекомендуемые значения скоростей сухого осаждения радионуклидов из атмосферы на подстилающую поверхность*

Вещество

, м/с

Элементарный йод (I2)

2·10–2

Органические соединения йода

1·10–4

Аэрозоли

8·10–3

ИРГ, 14C

0

3H (аэрозоль HTO)

3·10–2

3H (пар HTO)

0

* Значения скоростей сухого осаждения приняты:

для элементарного йода (I2), органических соединений йода и аэрозолей — в соответствии с Руководством по установлению допустимых выбросов радиоактивных веществ в атмосферу (ДВ-98). М.: Госкомэкология России, Минатом России, 1999;

для 3H (аэрозоль HTO) — в соответствии с Modelling the environmental transport of tritium in the vicinity of long term atmospheric and sub-surface sources // Report of the Tritium Working Group of the Biosphere Modelling and Assessment (BIOMASS) Programme. — Theme 3. — IAEA, 2003;

для 3H (пар HTO), 14C, ИРГ — в соответствии с Generic Models for use in Assessing the Impact of Discharges of Radioactive Substances to the Environment / Safety Reports. — Series No. 19. — Vienna: IAEA, 2000.

7. Среднегодовую постоянную вымывания радионуклида осадками рекомендуется рассчитывать по следующей формуле:

где:

 — абсолютная вымывающая способность осадков для радионуклида r, ч/(мм·с);

 — относительная вымывающая способность осадков типа s (s=1 для жидких осадков, s=2 для смешанных осадков и s=3 для твердых осадков);

 — среднегодовая сумма осадков типа s, мм.

Рекомендуемые значения величины  приведены в таблице № 16 настоящего приложения.

Таблица № 16. Рекомендуемые значения абсолютной вымывающей способности осадков

Вещество

Элементарный йод (I2)

1·10–5

Органические соединения йода

1·10–5

Аэрозоли

1·10–5

Инертные радиоактивные газы, 14C

0

3H (аэрозоль HTO)

1·10–5

3H (пар HTO)

0

Для параметра  рекомендуется принять следующие значения:  для жидких,  для смешанных,  для твердых осадков. Величина  оценивается по климатическим данным для района расположения источника выбросов.

В случаях, когда среднегодовое распределение осадков по типам (жидкие, твердые, смешанные) неизвестно, для определения среднегодовой постоянной вымывания радионуклидов рекомендуется консервативно использовать соотношение:

,

где  — суммарное среднегодовое количество осадков, мм.

8. Функцию истощения струи за счет радиоактивного распада рекомендуется определять по выражению:

где:

 — постоянная радиоактивного распада радионуклида r, с-1;

Uj,k — модуль скорости ветра на высоте выброса, м/с.

9. В случае, если в выбросе из i-го источника присутствуют изотопы природного урана (234U, 235U и 238U), рекомендуется для данных радионуклидов принимать  равной 1.

10. В случае, если в выбросе из i-го источника присутствуют изотопы природного урана (234U, 235U и 238U), рекомендуется не учитывать образование дочерних продуктов распада данных радионуклидов после выброса.

11. Функцию истощения струи за счет процессов вымывания атмосферными осадками рекомендуется определять по выражению:

12. В случае, если в выбросе из i-го источника присутствуют изотопы природного урана (234U, 235U и 238U), рекомендуется для данных радионуклидов принимать  равной 1.

13. Функцию истощения вследствие сухого осаждения рекомендуется определять выражением:

На расстояниях, где =, рекомендуется использовать выражение:

где  — максимальная высота слоя перемешивания, м (рекомендуется принимать равной 1,25·);

xmax — расстояние, на котором  достигает максимума .

14. В случае, если в выбросе из i-го источника присутствуют изотопы природного урана (234U, 235U и 238U), рекомендуется для данных радионуклидов принимать  равной 1.

15. Полную функцию истощения струи рекомендуется определять следующим выражением:

.

16. Параметр xвj,k рекомендуется определять как корень следующего уравнения:

где:

j — номер градации категории устойчивости атмосферы;

Vo — объемная скорость истечения газоаэрозольной примеси, м3/с;

Uj,k — скорость ветра на высоте выброса, м/с;

и  — дисперсии струи в горизонтальном и вертикальном направлениях, вычисленные для расстояния xвj,k, м.

Для поперечной дисперсии  рекомендуется использовать формулу:

Рекомендуемые значения параметра  для различных категорий устойчивости атмосферы приведены в таблице № 17 настоящего приложения.

Таблица № 17. Значения параметра c3 j для различных категорий устойчивости атмосферы

Категория устойчивости

A

B

C

D

E

F

G

c3 j

0,22

0,16

0,11

0,08

0,06

0,06

0,06

17. После определения  расчет объемных активностей рекомендуется проводить по формулам для точечных источников, заменяя в них реальные расстояния x от точки выброса до точки детектирования суммой .

18. Расчет для низких труб рекомендуется проводить по смешанной модели, где доля примеси от общего количества выброса, равная 1 — Kb, принимается выброшенной из высокой трубы, а доля примеси, равная Kb, принимается поступившей в зону аэродинамической тени, где формируется объемный источник. Рекомендуется принимать, что все выбросы из проемов здания и других, расположенных вблизи здания источников, высота которых ниже высоты здания, попадают в зону его аэродинамической тени.

Рекомендуемые значения доли выброса Kb, попадающей в зону аэродинамической тени за зданием при низком выбросе, в зависимости от безразмерной приведенной высоты здания , приведены в таблице № 18 настоящего приложения.

Таблица № 18. Значения доли выброса Kb, попадающей в зону аэродинамической тени за зданием при низком выбросе, в зависимости от безразмерной приведенной высоты здания

, м

Kb

≤0

1

0,05

0,984

0,1

0,960

0,2

0,906

0,3

0,808

0,4

0,662

0,5

0,5

0,6

0,338

0,7

0,192

0,8

0,094

0,9

0,040

0,95

0,014

≥1

0

19. Приведенную высоту здания , зависящую от взаимного расположения здания и трубы, рекомендуется рассчитывать по формуле:

где:

hs — геометрическая высота источника выбросов от поверхности земли, м;

hb — высота здания, м;

— расстояние от уровня земли до верхней границы зоны смещения потока воздуха за зданием, м, рассчитываемое по формуле:

где b — ширина перпендикулярного направлению ветра сечения здания, м.

Приложение № 4

к руководству по безопасности при использовании атомной энергии «Рекомендуемые методы расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов радиоактивных веществ в атмосферный воздух», утвержденному приказом Федеральной службы по экологическому, технологическому и атомному надзору от 30 августа 2021 г. № 288.

Пример расчета параметров, необходимых для разработки и установления нормативов предельно допустимых выбросов

1. Данное приложение содержит пример расчета функций перехода, связывающих значение годового выброса с создаваемой им годовой эффективной дозой, с использованием соотношений, приведенных в настоящем Руководстве по безопасности.

2. Рассмотрим следующий набор исходных данных:

1) источник выбросов — вентиляционная труба высотой hs=150 м, диаметр устья трубы D=6,5 м. Скорость истечения выброса w0=4,4 м/с, расход воздуха через устье — 529 000 м3/ч, температура выбрасываемой смеси T=28 оС. Режим работы источника — 24 ч/день, 365 дней в году;

2) радионуклидный состав и годовой объем выбросов приведены в таблице № 19 настоящего приложения;

3) санитарно-защитная зона представляет собой окружность радиусом 3 км с центром в точке расположения источника; сельскохозяйственных производств в пределах санитарно-защитной зоны нет, а за пределами санитарно-защитной зоны располагаются сельскохозяйственные угодья, используемые исключительно для выращивания плодоовощной продукции, годовое потребление которой взрослым населением составляет 65 кг/год;

4) квота от предела годовой эффективной дозы облучения населения составляет 100 мкЗв/год;

5) повторяемость направлений ветра в различных румбах и среднегодовая скорость ветра на высоте флюгера приведены в таблице № 20 настоящего приложения; годовые атмосферные осадки в районе расположения источника приведены в таблице № 21 настоящего приложения. Коэффициент мезомасштабной шероховатости z0=1 м.

Таблица № 19. Радионуклидный состав и годовой объем выбросов

Радионуклид

Q, Бк/год

3H (HTO)

3,2∙1010

41Ar

4,5∙1013

60Co

1,8∙107

131I (аэрозольная форма)

7,7∙108

90Sr

2,3∙105

134Cs

1,7∙106

137Cs

1,3∙107

Таблица № 20. Повторяемость направлений ветра в различных румбах и среднегодовая скорость ветра на высоте флюгера (откуда дует ветер)

Роза ветров, %

С

8

СВ

9

В

10

ЮВ

10

Ю

12

ЮЗ

21

З

17

СЗ

13

Среднегодовая скорость ветра, м/с

1,8

Среднегодовая температура воздуха, ºС

4,8

Таблица № 21. Годовые атмосферные осадки в районе расположения источника

Тип осадков

Количество, мм/год

Жидкие

464

Твердые

180

Смешанные

56

Сумма

700

3. В таблице № 22 приведены значения радиоэкологических параметров, которые будут использоваться в расчетах.

Таблица № 22. Значения радиоэкологических параметров, используемые в расчетах

Период полураспада, с

3,88∙108

6,58∙103

1,66∙108

6,93∙105

9,07∙108

6,49∙107

9,51∙108

,

‒*

7,85∙10–14

1,50∙10–13

2,31∙10–14

4,93∙10–16

9,25∙10–14

3,52∙10–14

,

‒*

‒*

1,95∙10–15

3,23∙10–16

7,96∙10–18

1,28∙10–15

5,01∙10–16

,

‒*

0

1,20∙10–8

7,20∙10–8

5,00∙10–8

6,60∙10–9

4,60∙10–9

Критическая группа по ингаляции

‒*

‒**

12–17 лет

1–2 года

12–17 лет

>17 лет

>17 лет

,

‒*

0

2,70∙10–8

1,80∙10–7

8,00∙10–8

1,90∙10–8

1,30∙10–8

Критическая группа по пероральному поступлению

‒*

‒**

1–2 года

1–2 года

12–17 лет

>17 лет

>17 лет

Fνr

‒*

0

8,00∙10–2

2,00∙10–2

3,00∙10–1

3,00∙101

3,00∙101

Fmмолоко, r, сут/л

‒*

0

1,00∙10–2

1,00∙10–2

3,00∙10–3

1,00∙10–2

1,00∙10–2

Ffмясо, r, сут/кг

‒*

0

7,00∙10–2

5,00∙10–2

1,00∙10–2

5,00∙10–2

5,00∙10–2

Fν1r

‒*

0

2,00∙100

1,00∙10–1

1,00∙101

2,00∙101

2,00∙101

, м/с

3,00∙10–2

0

8,00∙10–3

8,00∙10–3

8,00∙10–3

8,00∙10–3

8,00∙10–3

, ч/(мм∙с)

1,00∙10–5

0

1,00∙10–5

1,00∙10–5

1,00∙10–5

1,00∙10–5

1,00∙10–5

λs,r, сут-1

0

0

0

0

1,40∙10–4

1,40∙10–4

1,40∙10–4

, м2∙год/кг

0

0

1,20∙10–2

2,48∙10–6

1,30∙10–2

1,20∙10–2

1,30∙10–2

, м2∙год/кг

0

0

2,22∙10–3

1,02∙10–9

1,40∙10–2

2,74∙10–1

1,38∙100

,

2,60∙10–8

‒*

‒*

‒*

‒*

‒*

‒*

* Значение не установлено, поскольку для 3H используются расчетные модели, отличные от расчетных моделей для других радионуклидов.

** Для радионуклидов группы ИРГ отсутствует облучение по указанному пути.

4. Для того, чтобы определить необходимость установления нормативов для источника, а также перечень радионуклидов в выбросах рассматриваемого источника, для которых должны быть установлены нормативы, потребуется выполнить расчеты годовой эффективной дозы без учета рассеивания с помощью соотношений (21)–(25) раздела III настоящего Руководства по безопасности и оценить, какой вклад в нее дает каждый из указанных в таблице № 19 радионуклидов.

Суммарное с учетом всех радионуклидов значение годовой эффективной дозы без учета рассеивания для рассматриваемого источника выброса составляет 26 мЗв/год. Таким образом, в соответствии с критерием, установленным в пункте 7 Методики, для данного источника должны быть установлены нормативы.

Результаты оценки вклада отдельных радионуклидов представлены в таблице № 23.

Таблица № 23. Результаты определения перечня нормируемых радионуклидов

41Ar

2,30∙10–2

0

0

0

2,30∙10–2

90,14

137Cs

2,96∙10–9

1,66∙10–4

1,05∙10–7

1,92∙10–3

2,09∙10–3

8,11

60Co

1,77∙10–8

3,27∙10–4

3,40∙10–7

1,21∙10–5

3,40∙10–4

1,32

134Cs

1,02∙10–9

9,28∙10–6

1,96∙10–8

3,26∙10–5

4,19∙10–5

0,16

131I

1,13∙10–7

1,27∙10–5

2,27∙10–5

5,87∙10–7

3,61∙10–5

0,14

3H

–

–

–

–

2,99∙10–5

0,12

90Sr

7,49∙10–13

4,62∙10–8

1,81∙10–8

1,83∙10–6

1,90∙10–6

0,007

Из таблицы № 23 видно, что 99 %-ный вклад в годовую дозу обуславливают три радионуклида — 41Ar, 137Cs и 60Co, поэтому установление нормативов ПДВ требуется только в их отношении. Вклад в годовую эффективную дозу остальных радионуклидов не превышает 1 %, поэтому они могут быть исключены из дальнейшего рассмотрения.

5. С учетом приведенных в пункте 2 настоящего приложения исходных данных, а также принимая во внимание, что для рассматриваемой трубы высотой 150 м отсутствует необходимость учета влияния зданий, формула для расчета среднегодового метеорологического фактора разбавления (2) приложения № 1 к настоящему Руководству по безопасности примет следующий вид:

Порядок расчета величин, входящих в формулу (1), описан в приложении № 3 к настоящему Руководству по безопасности.

6. С учетом того, что в исходных данных принято, что коэффициент мезомасштабной шероховатости поверхности z0=1 м, для расчета вертикальной дисперсии струи выброса σz,j (x) для различных категорий устойчивости атмосферы используется параметризация Смита-Хоскера, описанная формулами (1)–(3) приложения № 3 к настоящему Руководству по безопасности.

На рисунке 1 настоящего приложения приведены графики зависимостей σz,j(x) для различных категорий устойчивости атмосферы в логарифмическом масштабе.

Рис. 1. Графики зависимостей  для различных категорий устойчивости атмосферы

7. Рассчитанные на высоте выброса в соответствии с формулой (11) приложения № 3 к настоящему Руководству по безопасности значения скорости ветра  для различных категорий устойчивости приведены в таблице № 24 настоящего приложения.

Таблица № 24. Рассчитанные на высоте выброса значения скорости ветра  для различных категорий устойчивости

, м/с

2,8

2,9

3,1

3,7

4,2

5,6

9,1

8. Подъем струи над источником выброса Δhj (x), м, для различных категорий устойчивости атмосферы рассчитывается с помощью формул (12)–(14) приложения № 3 к настоящему Руководству по безопасности.

На рисунке 2 настоящего приложения приведены в логарифмическом масштабе графики зависимостей Δhj (x) для различных категорий устойчивости атмосферы, построенные по формулам (12)–(14) приложения № 3 к настоящему Руководству по безопасности.

Рис. 2. Графики зависимостей Δhj (x) для различных категорий устойчивости атмосферы

9. Значения функции истощения струи  рассчитываются с использованием формул (17)–(21) приложения № 3 к настоящему Руководству по безопасности.

Значение среднегодовой постоянной вымывания радионуклидов осадками, рассчитанное с использованием исходных данных из таблицы № 21 настоящего приложения по формуле (15) приложения № 3 к настоящему Руководству по безопасности для радионуклидов 137Cs и 60Co составляет 1,3·10–6 с–1. Для 41Ar значение данного параметра равно нулю.

Значения скоростей сухого осаждения в соответствии с таблицей № 15 приложения № 3 к настоящему Руководству по безопасности принимаются равными 8·10–3 м/с для 137Cs и равными нулю для 41Ar.

На рисунках 3–5 для 41Ar, 137Cs и 60Co приведены графики зависимостей полных функций истощения струи  за счет радиоактивного распада, вымывания атмосферными осадками и сухого осаждения для различных категорий устойчивости атмосферы.

Рис. 3. Графики зависимостей функции истощения для 41Ar от расстояния от источника для различных категорий устойчивости атмосферы

Рис. 4. Графики зависимостей функции истощения для 137Cs от расстояния от источника для различных категорий устойчивости атмосферы

Рис. 5. Графики зависимостей функции истощения для 60Co от расстояния от источника для различных категорий устойчивости атмосферы

10. На рисунках 6–13 приведены графики зависимостей среднегодовых метеорологических факторов разбавления, определяемых формулой (1) пункта 5 данного приложения, для каждого из восьми направлений ветра, приведенных в таблице № 20 настоящего приложения.

Рис. 6. Графики зависимостей фактора разбавления от расстояния от источника в южном направлении

Рис. 7. Графики зависимостей фактора разбавления от расстояния от источника в юго-западном направлении

Рис.8. Графики зависимостей фактора разбавления от расстояния от источника в западном направлении

Рис. 9. Графики зависимостей фактора разбавления от расстояния от источника в северо-западном направлении

Рис. 10. Графики зависимостей фактора разбавления от расстояния от источника в северном направлении

Рис. 11. Графики зависимостей фактора разбавления от расстояния от источника в северо-восточном направлении

Рис. 12. Графики зависимостей фактора разбавления от расстояния от источника в восточном направлении

Рис. 13. Графики зависимостей фактора разбавления от расстояния от источника в юго-восточном направлении

Из анализа графиков, представленных на рисунках 6–13 настоящего приложения, следует, что максимальные значения факторов разбавления реализуются в северо-восточном направлении от источника.

11. В таблице № 25 настоящего приложения приведены рассчитанные значения  для 41Ar, 60Co и 137Cs в северо-восточном направлении от источника выбросов, рассчитанные по формуле (5) приложения № 1 к настоящему Руководству по безопасности.

Таблица № 25. Рассчитанные значения для 41Ar, 60Co и 137Cs в северо-восточном направлении от источника выбросов

Расстояние от источника x, м

, с/м2

41Ar

60Co

137Cs

500

1,89∙10–4

1,93∙10–4

1,92∙10–4

1 000

9,27∙10–5

9,62∙10–5

9,61∙10–5

1 500

6,07∙10–5

6,40∙10–5

6,40∙10–5

2 000

4,46∙10–5

4,79∙10–5

4,79∙10–5

3 000

2,87∙10–5

3,18∙10–5

3,18∙10–5

4 000

2,07∙10–5

2,38∙10–5

2,38∙10–5

5 000

1,59∙10–5

1,89∙10–5

1,89∙10–5

6 000

1,28∙10–5

1,57∙10–5

1,57∙10–5

7 000

1,06∙10–5

1,35∙10–5

1,35∙10–5

9 000

7,61∙10–6

1,04∙10–5

1,04∙10–5

11 000

5,77∙10–6

8,48∙10–6

8,48∙10–6

13 000

4,52∙10–6

7,14∙10–6

7,14∙10–6

15 000

3,63∙10–6

6,17∙10–6

6,17∙10–6

12. Рассчитанные в соответствии с формулами (3) и (4) приложения № 1 к настоящему Руководству по безопасности среднегодовые метеорологические факторы сухого осаждения Fr,n(x) и влажного выведения Wr,n(x) для 60Co и 137Cs в северо-восточном направлении от источника представлены в таблице № 26 настоящего приложения. Для 41Ar значения этих функций равны нулю ввиду того, что значения скорости сухого осаждения и постоянной вымывания осадками для этого радионуклида равны нулю.

Таблица № 26. Рассчитанные значения Fr,n (x) и Wr,n (x) для 60Co и 137Cs

Расстояние от источника x, м

Fr,n (x), м–2

Wr,n (x), м–2

500

4,49∙10–10

2,50∙10–10

1 000

9,13∙10–10

1,25∙10–10

1 500

7,06∙10–10

8,32∙10–11

2 000

5,14∙10–10

6,22∙10–11

3 000

3,44∙10–10

4,13∙10–11

4 000

3,33∙10–10

3,09∙10–11

5 000

2,95∙10–10

2,46∙10–11

6 000

2,55∙10–10

2,05∙10–11

7 000

2,20∙10–10

1,75∙10–11

9 000

1,67∙10–10

1,35∙10–11

11 000

1,31∙10–10

1,10∙10–11

13 000

1,06∙10–10

9,29∙10–12

15 000

8,80∙10–11

8,02∙10–12

13. С учетом того, что в исходных данных принято, что санитарно-защитная зона представляет собой окружность радиусом 3 км с центром в точке расположения источника, формула (1) раздела II настоящего Руководства по безопасности для расчета функции перехода, связывающей активность выброса радионуклида r из i-го источника с годовой эффективной дозой облучения населения, примет следующий вид:

Функции перехода  рассчитываются по формулам (2), (3), (4) и (5) раздела II настоящего Руководства по безопасности.

14. В таблице № 27 приведены максимальные значения функций перехода , связывающих величину годового выброса 41Ar, 60Co и 137Cs с создаваемыми ими годовыми эффективными дозами, с указанием точки местности, где они реализуются.

Таблица № 27. Результаты расчета функций перехода

Радионуклид

, Зв/Бк

Расстояние от источника (на северо-восток), м

41Ar

8,47∙10–21

930

60Co

1,34∙10–16

3 138

137Cs

1,41∙10–15

3 138

15. Полученные значения функций перехода можно использовать для расчета нормативов ПДВ с помощью соотношения: